Payment & Shipping Terms:
|Construction:||Bag Filter||Weight:||According To Different Size|
|Size:||As Per Request||Color:||According To Different Class|
|Supply Ability:||500 Piece/Pieces Per Week|
Pocket Type Air filter Bag Filter For Air Conditioner System F5 F6 F7 F8 F9
|Principle||Vacuum filtration||Use:||Air filtration|
|Suitable||Air||Nature||High hygiene requirements|
|Type||New||Application||Chemical, pharmaceutical, automotive, light industry, food|
The bag filter has large effective filtering area, large dust holding capacity, small resistance and large ventilation. The frame and the support frame can be reused. When the filter is replaced, only the filter bag needs to be replaced, which is convenient and quick, and greatly reduces the running cost. It is widely used in the filtration systems of electronics, pharmaceutical, medical, food and other industries. It is the best medium efficiency filter at present.
It can be used for the intermediate filtration of the air conditioning system to protect the lower-stage filter and the system itself in the system. In places where the air purification and cleanliness requirements are not strict, the air treated by the medium-efficiency filter can be directly sent to the user. The aluminum frame bag filter adopts high-quality synthetic fiber or imported glass fiber as the filter material, aluminum alloy profile frame and internal sprayed cold wire drawing support frame.
Under the rated air volume conditions, the filter needs to be replaced within 3-4 months; or when the resistance of the filter reaches 400Pa or more, the filter must be replaced; if the filter uses a cleanable filter material, replace it. The filter material can be rinsed with water or a solution containing a neutral detergent, dried and then replaced; at most it can be washed twice, that is, a new filter must be replaced; if the dust concentration in the environment is large, this is The life cycle will also decrease.
1. Regularly check the inlet surface of the filter for any obstruction of impurities and the surface of the filter material for damage;
2. If there is any object blocking the surface, it should be removed;
3. If the surface of the filter material is seriously damaged, it must be replaced with a new filter material or replaced with a new one;
4. When the filter is installed, it is necessary to ensure good sealing with the crimping part of the frame to prevent leakage of air volume;
5. Do not use heavy objects to hit the surface of the filter. Do not use force to pull the filter surface of the filter.
6. When installing, the length of the filter bag should be perpendicular to the ground to ensure the filtering effect and increase the service life of the air supply.
(F5, 45%, white, for medium efficiency filter pre-filter)
(F6, 65%, orange, used in commercial buildings, theaters, stations, airports)
(F7, 85%, green, for spray booths, schools, computer rooms)
(F8, 95%, pink, for industrial, pharmaceutical, food, hospital)
(F9, 98%, yellow, for precision electronics industry, defense factory, sterile room)
Rated air flow
95- 98% F9
Contact Person: Allan